Nate, the instructions say this:
"Installing the Wall Switch Module (3-way applications, diagram B)
? Disconnect the power at the circuit breaker.
? Remove the wall plates and unscrew the existing switches from their boxes.
? Locate the Neutral wire in your switch box (this is a white wire, NOT a bare copper wire). Connect this white Neutral wire to the
NEUTRAL terminal on the WS13A.
? Identify the common wire at each existing switch (usually connected to a different color terminal).
? Replace one of the existing wall switches with the WS13A Wall Switch (Master): connect the common wire to the LIVE terminal
on the WS13A. Connect one of the "traveller wires" to the LOAD terminal on the WS13A. Connect the other Traveller to the
CONTROL terminal on the WS13A. If one of the travellers is red connect it to CONTROL on the WS13A.
? Replace the other existing wall switch with the WS14A Companion Switch (sold separately): connect the common wire to one of
the WS14A's terminals labelled LIVE. Connect the (red) traveller which you connected to the CONTROL terminal on the WS12A
to the terminal labelled SWITCH on the WS14A. Connect the remaining traveller wire to the second terminal labelled LIVE on the
WS14A. Screw both switches into their wall boxes and replace the wall plates."
Get where i'm pulling my wiring idea from?
while reading draw a diagram, then compare this to the one in the link in the other post i made...let m eknow if they match
The romex idea didn't work, i'll try again though...could master really be blown? it still works?